Altivar 61 And Altivar 61 Plus Variable Speed Drives Page 58 Input Power Options

58 Altivar 61 variable speed drives Passive filters Input Power Options Passive filters A passive filter is used to reduce current harmonics with total harmonic distortion factors of less than 16% or 10%. These performance levels can be improved still further and the harmonic distortion reduced to less than 10% or 5% if the filter is used with a DC choke. The reactive power increases at no load or low load. To eliminate this reactive power, the filter capacitors can be disconnected via the drive. The degree of protection of the passive filters is IP 20. ATV61H ppp M3, ATV61H ppp Y and ATV61H ppp S6X drives are not compatible with the use of these passive filters. It is recommended or mandatory, depending on the rating, to use a line choke. Applications Reduction of current harmonics in order to use drives in the first environment (restricted distribution, for domestic use, sale conditional on the competence of the user and the distributor in terms of reduction of current harmonics). L1 L2 L3 Passive filter ATV61 pppp N4 ATV61W ppp N4C Motor rating For ATV61 drives Line Supply Filter Filter Quan- tity per Drive Part Number (2) Packaging Size Weight Line Current Input Current Output Current L x L x H Net kw HP A inches cm lbs kg THDI 16% (1) 0.75 1 ATV61H075N4 2.5 6 6.2 1 VW3A46139 23.6 x 15.7 x 20.1 60 x 40 x 51 22 10 1.5 2 ATV61HU15N4 3 6 6.2 1 VW3A46139 23.6 x 15.7 x 20.1 60 x 40 x 51 22 10 2.2 3 ATV61HU22N4 5 6 6.2 1 VW3A46139 23.6 x 15.7 x 20.1 60 x 40 x 51 22 10 3 - ATV61HU30N4 6 6.2 1 VW3A46139 23.6 x 15.7 x 20.1 60 x 40 x 51 22 10 4 5 ATV61HU40N4 7 10 10.4 1 VW3A46140 23.6 x 15.7 x 20.1 60 x 40 x 51 29.8 13.5 5.5 7.5 ATV61HU55N4 10 10.4 1 VW3A46140 23.6 x 15.7 x 20.1 60 x 40 x 51 29.8 13.5 7.5 10 ATV61HU75N4 13 14 14.5 1 VW3A46141 23.6 x 15.7 x 20.1 60 x 40 x 51 35.9 16.3 11 15 ATV61HD11N4 19 19.5 1 VW3A46142 23.6 x 15.7 x 20.1 60 x 40 x 51 48.5 22 15 20 ATV61HD15N4 24 25 26 1 VW3A46143 23.6 x 15.7 x 20.1 60 x 40 x 51 50.7 23 18 25 ATV61HD18N4 32 31 32 1 VW3A46144 31.5 x 23.6 x 24 80 x 60 x 61 72.8 33 22 30 ATV61HD22N4 35 36 37.5 1 VW3A46145 31.5 x 23.6 x 24 80 x 60 x 61 81.6 37 30 40 ATV61HD30N4 44 48 50 1 VW3A46146 31.5 x 23.6 x 24 80 x 60 x 61 83.8 38 37 50 ATV61HD37N4 58.7 60 62.5 1 VW3A46147 31.5 x 23.6 x 24 80 x 60 x 61 94.8 43 45 60 ATV61HD45N4 68 73 76 1 VW3A46148 31.5 x 23.6 x 24 80 x 60 x 61 121.3 55 55 75 ATV61HD55N4 82.6 95 99 1 VW3A46149 31.5 x 23.6 x 24 80 x 60 x 61 136.7 62 75 100 ATV61HD75N4 108 118 122.5 1 VW3A46150 31.5 x 23.6 x 24 80 x 60 x 61 163.1 74 (1) Adding a DC choke can redue THDI to <5%. (2) Filters are rated for 460V 60Hz three phase power supply.

Previous PageNext Page