PowerPact B-Frame 15 to 125 A Circuit Breakers Installation in Equipment
Exposed Conductor Safety Clearance An insulating screen or long terminal shield is required if: 2, 3, or 4 poles C < 9.5 mm (< 0.37 in.), Customer-provided insulation material required if: 1 pole C < 12.7 mm (<0.5 in.).
Circuit Breaker Enclosures, Enclosure Accessories (Available Late 2017)
Square D brand circuit breaker enclosures are UL Listed/CSA Certified and are suitable for use as service entrance equipment. The short circuit rating of an enclosed circuit breaker is equal to the rating of the circuit breaker installed. Circuit breakers are ordered and shipped separately for field installation. Circuit Breaker Enclosure Catalog Numbers
Device Information Enclosure Catalog No. Neutral Kit Catalog No. Service Ground Kit Device Poles NEMA 1 Flush NEMA 1 Flush 304 Stainless Steel Front NEMA 1 Surface NEMA 3R Circuit Breaker 1, 2, 3 B125F B125FSS B125S B125RB SN100FA PKOGTA2 NEMA 4X, 5 Type 304 Stainless Steel NEMA 4X, 5 Type 316 Stainless Steel NEMA 12K Without Knockouts NEMA 4X Without Knockouts Circuit Breaker 1, 2, 3 B125DS B125SS B125A B125AWK SN100FA PKOGTA2 Molded Case Switch 1, 2, 3 - - B125WKMC - -
62 0611CT1603Previous Page